Client Waste plant operator
Location Birmingham, UK
Simulate grid connection for waste plant commissioning
A global water and natural resources company wanted to get their new waste plant commissioned and accredited as soon as possible. The problem was, they were having trouble connecting to the main grid because of a faulty connector.
They couldn’t wait for the connector to be fixed. They had to meet tight accreditation deadlines set by the Renewables Obligations scheme and they needed to move fast to obtain their Renewable Obligations Certificates (ROC) before the government scheme closed. So what do you when you don’t have a real connection supply to test your system? You ask us to build you a replica.
Project fact file
Deadline for design and installation
Turbine to be tested and commissioned
High-voltage power and loadbank package
We got our specialist high-voltage team on site as quickly as possible. They only had one week to design and install a package that would result in the customer’s plant being commissioned.
We used a high-voltage power and loadbank package to simulate a connection supply. This enabled the plant’s 10 MW steam turbine to be tested and commissioned. The turbine did not have a star point earthing system so, for safety’s sake, we installed a separate earthing system as a temporary package. Double-stacked transformers and loadbanks were used to save space in the small area and to allow access.
the aggreko difference
We can react quickly to customer requirements, no matter how specialised.
Accreditation deadlines met – export to the grid accelerated
We delivered the specially designed package within the tight timeframe of one week. By using a temporary high-voltage power solution to simulate a grid connection the customer was able to overcome commissioning delays.
It proved that the waste plant would be able to plug into the grid once the connector was fixed, meeting the valuable ROC deadline. This, in turn, enabled the plant to accelerate export of power to the main grid and begin contributing.
“This was one of those projects where time was non-negotiable. The customer had to have complete confidence that our expert team of engineers could come up with a package in just one week. We’re happy to say we did just that.”